Small crack in pipeline may have delayed oil spill detection
HUNTINGTON BEACH, Calif. (AP) — Video of the ruptured pipeline that spilled tens of thousands of gallons of crude oil off Southern California shows a thin crack along the top of the pipe that could indicate a slow leak that initially was difficult to detect, experts said Thursday.
The 13-inch-long (33-centimeter) narrow gash could explain why signs of an oil slick were seen Friday night but the spill eluded detection by the pipeline operator until Saturday morning, they said.
“My experience suggests this would be a darned hard leak to remotely determine quickly,” said Richard Kuprewicz, a private pipeline accident investigator and consultant. “An opening of this type, on a 17-mile-long (27-kilometer) underwater pipe is very hard to spot by remote indications. These crack-type releases are lower rate and can go for quite a while.”
When pipes experience a catastrophic failure, the breach typically is much bigger, what’s referred to in the industry as a “fish mouth” rupture because it gapes wide like the mouth of a fish, he said.
Amplify Energy, a Houston-based company that owns and operates three offshore oil platforms and the pipeline south of Los Angeles, said it didn’t know there had been a spill until its workers detected an oil sheen on the water Saturday at 8:09 a.m.
The cause of the spill is under investigation by numerous agencies as the cleanup continues along miles of shoreline on the Orange County coast south of the ports of Los Angeles and Long Beach.
The Coast Guard on Thursday slightly revised spill estimates to at least about 25,000 gallons (95,000 liters) and no more than 132,000 gallons (500,000 liters).
The Coast Guard on Thursday said it is investigating the incident with other agencies as a “major marine casualty” due to the potential involvement of a vessel and damages exceeding $500,000. It said they will determine if criminal charges, civil penalties or new laws or regulations are needed.
Investigators are looking into whether a ship waiting to offload its cargo snagged and bent the pipeline with its anchor.
Coast Guard investigators boarded the massive German-flagged container ship Rotterdam Express on Wednesday to determine if it was involved in the spill. The Rotterdam was the ship anchored closest to the pipeline last week.
Hapag-Lloyd, the shipping company that operates the vessel, confirmed Thursday that investigators boarded the ship while it was docked at the Port of Oakland in San Francisco Bay. The Coast Guard interviewed the captain and crew and was provided access to the logbook showing the ship’s locations, according to Nils Haupt, a spokesman at Hapag-Lloyd’s headquarters in Hamburg, Germany.
Afterward, the Coast Guard called the company to say the Rotterdam no longer was under scrutiny for the spill, Haupt said. The ship was cleared to depart Oakland was headed to Mexico.
The leak occurred about 5 miles (8 kilometers) offshore at a depth of about 98 feet (30 meters), investigators said. A 4,000-foot (1,219-meter) section of the pipeline was dislodged 105 feet (32 meters), bent back like the string on a bow, Amplify’s CEO Martyn Willsher has said.
Jonathan Stewart, a professor of civil and environmental engineering at the University of California, Los Angeles, said he was surprised the damage wasn’t more severe given how far the pipe was moved.
“My first reaction when I heard that it is displaced so far was that it’s remarkable that it’s even intact at all,” Stewart said.
Questions remain about when the oil company knew it had a problem and delays in reporting the spill.
A foreign ship anchored in the waters off Huntington Beach reported to the Coast Guard that it saw a sheen longer than 2 miles (3.2 kilometers) just after 6 p.m. A satellite image shot by the European Space Agency indicated a likely oil slick in the area around 7 p.m., which was reported to the Coast Guard at 2:06 a.m. Saturday after being reviewed by a National Oceanic and Atmospheric Administration analyst.
Federal pipeline safety regulators have put the time of the incident at 2:30 a.m. Saturday but say the company didn’t shut down the pipeline until 6:01 a.m. and didn’t report the leak to the Coast Guard until 9:07 a.m. Federal and state rules require immediate notification of spills.
Willsher, who took questions alongside Coast Guard and other officials over four days, did not show up at Thursday’s news conference. Other officials declined to explain his absence.
The type of crack seen in the Coast Guard video is big enough to allow some oil to escape to potentially trigger the low pressure alarm, Kuprewicz said. But because the pipeline was operating under relatively low pressure, the control room operator may have simply dismissed the alarm because the pressure was not very high to begin, he said.
Ramanan Krishnamoorti, a petroleum engineering professor at the University of Houston, said the pipeline might have leaked for days before being discovered.
“If you have a massive crack or massive hole, you get a huge pressure drop and therefore you know you have a massive leak,” he said. “When you have a hairline crack like that, perhaps this could have been going on for two, three, four days.”
The fact that the San Pedro Bay line was still encased in concrete in the video is another indication that oil was likely leaking at a low rate. A major breach on a highly pressurized line would blow the concrete off, Kuprewicz said.
A second underwater video released Thursday showed a broader view of a bent section of pipeline. Long indentations in the sand can be seen intersecting with one side of the pipe at the point of the bend, but do not appear to continue on the far side of the line.
“That’s pretty revealing,” Krishnamoorti said. “It seems to me you’ve got something that was dragged in the sand that might have impacted the pipeline.”
But he remained puzzled that the leak came from a crack and not a larger gash, assuming it was hit by an anchor or some other object.
A crack suggests the pipe, which was installed in 1980, perhaps withstood an initial impact, but had been weakened over time by corrosion and become more prone to fail, Krishnamoorti said. That means Amplify would have some responsibility for it failing.
Because the line is encased in concrete — a means of keeping it weighted down on the sea floor — the Coast Guard video doesn’t reveal the condition of the half-inch-thick steel pipe underneath.
Once federal safety investigators cut out the damaged section of pipe and remove it, they will be able to conduct a closer examination, looking for signs of corrosion, metal fatigue or other anomalies that would have made it more susceptible to failure. That examination should also reveal if the crack grew larger over time, Kuprewicz said.
Associated Press writers Michael Biesecker and Michael Balsamo contributed from Washington. Michael R. Blood contributed from Los Angeles.
Copyright 2021 The Associated Press. All rights reserved.